SIMATIC S, ANALOG INPUT SM ,. GALVANICALLY ISOLATED, 8 AI, 14 BIT,. MS/CHANNEL, CURRENT, VOLTAGE,. INTERRUPTS. Product data sheet. 6ESHFAB0. -. SIMATIC S, ANALOG INPUT SM ,. GALVANICALLY ISOLATED, 8 AI, 14 BIT. Buy Now Siemens 6ESHFAB0 brand new & guaranteed, at the best price. 6ES7 HFAB0 Siemens S, ANALOG INPUT SM , 8 AI.
|Published (Last):||20 July 2005|
|PDF File Size:||16.26 Mb|
|ePub File Size:||18.25 Mb|
|Price:||Free* [*Free Regsitration Required]|
Site Explorer Site Explorer. Currently trying to commission a Siemnes 331-7hf01-0wb0 and analogue card as above, can some please tell me if the wiring diagram is correct.
We have 5 2 wire mA signals, and the rest of the inputs are spare. This is universal card. You have to configure 2 331-7gf01-0ab0 or 4 wire along with voltage or current input in hardware configuration to read signals correctly.
Check also if the measuring range module is pluged right.
I’d see the connection diagram 331-hf01-0ab0but it didn’t show what to do with unused channels and I thought this might be the problemthe “manual” download does show how to wire these, so thanks for that. I think I’ve discovered the issue we might be having, the unit was installed to the drawings we were issued, but I’m pretty certain it’s a 4-wire system on the other end of the cables e6s7 not a 2-wire as the drawings suggest!
Anyhow, I’m 331-7hf01-0ba0 to switch the wiring around, and hope there’s been no damage to the card. I’ll post later and let you know how I got on. When the transducer have thier power-supply not from the AI-Module through the wires for the measurement, it is a 4-wire-transducer. I’m stuck in between wiring the panel to the drawings not knowing what’s connected at the other end: I have to say, Siemens don’t make it easy!
If for four wire you need to link all the negative sides of the signal to -ve, then why not do it within the square setting block you have to put in position to select the signal type.
We only have five signals, so according to the manual I need to shot out unused inputs, but the channel 5 again why start at 0!! New question published by tammu is split to a separate thread with the subject connect Th two wire transmitter with external power supply to 7KF02 AI 6rs7.
Taiwan SIEMENS 6ES7 HFAB0 |
Product Support Services Forum mySupport. Attachment Siemens Analogue Card. Follow us on Twitter Youtube.
Hi new to Siemens so please be gentle. Hi, This is universal card. Data Sheet and Wiring Manual chapter 5. This contribution was helpful to 1 thankful Users Markriko.
Siemens 6ESHFAB0 (6ESHFAB0) PLC | eBay
There is no bad feedback! This contribution was helpful to 2 thankful Users Towome Markriko. Thanks everyone for your help. I’m afraid this is what comes when too many people are involved with a project.
Siemens 6ES7331-7HF01-0AB0 (6ES7331-7HF01-0AB0) PLC
Once again thanks for helping out. This was indeed the problem, the drawing was for 2 wire, in reality the system was 4 wire!! Making links for 14 terminals is both time consuming and costly! Surely it wouldn’t be 331-7hf01-ab0 hard to enable monitoring on a per channel basis. Cheers, everyone for the help.